MasterHeat 240v wire is a simple, economical way to warm floors and provide years of lasting comfort. Warm all kinds of floor coverings including ceramic tile, stone, wood, laminates, vinyl and carpet. Whatever your installation, there is a MasterHeat in floor warming cable spool sized just for your project.
Our uncoated wire is flexible and easy to work with. Please be aware that it cannot be used in showers or wet areas. For showers or wet areas, use MasterHeat coated wire.
MasterHeat in floor heating wires can be spaced and attached with metal straps or with the Radiant Positioning Mats. In either case, pay special attention to how thin-set or self-leveling mortar should be applied over the cables prior to setting tile, stone, or other flooring.
Evaluate how many square feet of floor you would like to be heated by radiant heat. Do not put under cabinets or appliances. Generally, about 85%-90% of the open areas should have the floor warming element. Leave the in floor heating wire at least 4"-6" away from your walls. To keep toes warm, install right up to the toe-kick in front of kitchen or bath cabinets, and in front of a toilet, shower or tub.
- Twin-wire technology
- Single power lead
- Oxygen-free heating elements
- Aramid reinforcing fibers
- High-temp insulation
- Braided metal jacket
Spacing: Choose a "spacing factor" of 2", 2-1/2" or 3" on center
- 2" on center = 15 Watts/sq.ft. Use on concrete basement slabs, sunrooms and in other high heat loss areas
- 2-1/2" on center = 12 Watts/sq.ft. Use in bathrooms, kitchens, living/dining areas, etc.
- 3" on center = 10 Watts/sq.ft. Use in hallways, entries, low heat loss areas, etc.
2-1/2" spacing on center is the most commonly used spacing and equals the heat output of the MasterHeat in floor heating mats
The chart below for square footages for different wire spacing, and power draw.
|Item #||L/F||Sq.Ft @ 2" o.c. (15W/sq.ft)||Sq.Ft. @ 2.5" o.c. (12W/sq.ft.)||Sq.Ft @ 3" o.c. (10W/sq.ft)||Amp Draw|
|Warranty:||25 Year Limited Warranty|
|Net Weight (lbs.):||2.50 - 20.00|
1 Customer Reviews
- Just like the others!
I'm a professional tile installer and have Installed many electric radiant heat systems from Nuheat, King, and others. I put two runs (~300sf @3"oc ) of this 240v uncoated MasterHeat wire in my kitchen and dining room last fall. The wire quality appears to be nearly identical to the others and the installation went very smoothly. Careful installation is critical, as with any radiant heat system. Used around 30 bags of MWI's self-leveling (I had some big dips in my slab) and would recommend both of these products based on the quality and price. Nice to finally enjoy warm floors in the winter like so many of my clients rave about! Subtracted 1 star for lack of warranty info in the box.